The heat loss of exhaust smoke is the largest of all kinds of heat loss in boiler. Generally, the heat loss of exhaust smoke is 6% of the heat fed into the furnace, and the heat loss of exhaust gas increases 0.5% when the temperature of exhaust gas increases by 12 ℃ and 15 ℃. So the exhaust temperature is one of the most important indicators of boiler operation. The following are several possible causes of increased flue gas temperature in the furnace: (1) slagging and ash accumulation on the heated surface. No matter it is the slag accumulation in the water-cooled wall of the furnace, or the ash deposition in the superheater, convection tube bundle, economizer and preheater, the thermal resistance of the flue gas measurement will increase, the cooling effect of the flue gas will become worse due to the deterioration of the heat transfer, and the exhaust temperature will rise. (2) excess air coefficient Big. Under normal conditions, the exhaust temperature increases with the increase of excess air coefficient at furnace outlet. After the increase of excess air coefficient, although the amount of smoke increased, the rate of smoke increased, and the convection heat increased, the increase of heat transfer was not as much as that of the increase of flue gas. It can be understood that after the increase of smoke speed, the flue gas leaves the heating surface without time to transfer heat to the working fluid. (3) the air leakage coefficient is too large. The flue gas leakage in the furnace and rear shaft of a negative pressure boiler is inevitable and the leakage coefficient allowed by a certain heating surface is specified. When the air leakage coefficient increases, the effect on the exhaust temperature is similar to that of the superheated air coefficient. And the air leaks away. The closer the furnace is, the greater the influence on the rise in exhaust temperature. (4) Water supply temperature. When the steam turbine load is too low or the high pressure heater is out of line, the feed water temperature of the boiler will be lowered. Generally speaking, if the fuel quantity is kept constant, the heat transfer temperature difference of the economizer decreases and the heat absorption of the economizer decreases when the feed water temperature is increased, which makes the exhaust temperature increase. (5) moisture in the fuel. The increase of moisture in the fuel increases the amount of smoke, thus increasing the exhaust temperature. (6) Boiler load. Although the boiler load increases proportionally, the amount of smoke, the amount of steam, the amount of water supplied, and the volume of air increase proportionally, however, the flue gas temperature at the furnace outlet increases proportionally. Increase, so that the exhaust temperature increased. After increasing the load, the outlet temperature of the furnace increases, the heat transfer temperature difference of the convection heating surface increases and the heat absorption increases. Therefore, the more the convection heating surface is, the less the influence of the boiler load on the exhaust gas temperature is. (7) fuel varieties. When the low calorific value gas is fired, the radiative heat transfer in the furnace decreases due to the decrease of furnace temperature, and the non-combustible components in low calorific value gas, mainly N _ 2, CO _ 2 and H _ 2O, increase the amount of flue gas, so the exhaust temperature increases. Although the excess air coefficient of furnace outlet is lower than that of coal burning, the ash content in the fuel oil is very low after the pulverized coal furnace is changed to burn oil, although the excess air coefficient at the furnace outlet is lower when burning oil. There is no larger ash particle in flue gas, and there is no cleaning effect of larger ash particle on the heating surface, and the convection heating surface is polluted more seriously. Therefore, combustion is not good, often smoke-emitting boiler smoke temperature rise. When there is a steel ball dust removal device at the tail, the exhaust temperature is slightly lower than that of burning coal because the tail is cleaner. (8) the operation mode of pulverizing system. For a closed pulverizing system with a silo, when the pulverizing system is in operation, as a part of the water in the fuel enters the furnace, the furnace temperature decreases and the flue gas increases, and the cold air leaking into the pulverizing system enters the furnace as a primary air during the operation of the pulverizing system. Reduction of air flow through air preheater To raise the exhaust temperature. On the contrary, when the pulverizing system is shut down, the exhaust temperature decreases.
Boiler multiple protection: (1) the integration of boiler water level to protect water level and boiler design, the appearance of more compact appearance, accurately show the actual water level in the boiler body function. Coupled with dual independent electronic water level control system to achieve ultra-low water level in the boiler, low water level automatic adjustment function, the normal water level, high water level, ensure that the boiler in a variety of unforeseen circumstances foolproof, secure home. (2) steam pressure protection ☆ pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switch, other control lines or automatic control chain protection. Common pressure controller and pressure gauge, vapor pressure overpressure alarm can cut off the burner limit is reached; the pressure controller may be single or double fire burning fire the actual operating pressure regulator. ☆ safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition.
10 tons of horizontal gas 2 tons of hot water boiler safety features Henan party nearly 10 tons of gas hot water boiler can be divided according to the type of gas hot water boiler WNS and SZS gas hot water boiler, meaning both what is it? WNS means is a horizontal-type combustion chamber burner, meaning that double drum SZS vertical type burning furnace chamber, although the two different processes of different structures, but the fuel and the safety device are the same. This chapter focuses to introduce safety protection system of the two kinds of boiler: 1, interlock protection system ① As the two kinds of dual-use oil and gas boilers are in this together computing, once the fuel or air pressure below the minimum set when the standard, it will automatically cut off the fuel supply ② cold water delivery device event of a failure, will automatically cut off the fuel supply ③ water temperature is higher than the highest temperature setting, will automatically cut off the fuel supply 2, the most dangerous place is the ignition system boiler system , because many of these conditions could not be controlled once the ignition, so the first firing of the furnace should be purged to avoid residual combustible gas combustion furnace, after the purge, ignite pilot fuel (oil or gas) flame monitor reflects the flame existence, and it continues to burn about 10s. After 10s, the main fuel valve (oil or gas) driven i.e., ignite the main burner. If the normal main burner combustion, the ignition system is automatically shut down. 3, turn off the boiler system we know if it is to continue to provide fuel to the furnace in the flame will cause serious consequences of an explosion, this one so fast Henan party made a special detection device, or burn when the ignition fails halfway flameout, general in the 5S (ignition) or the 10s (runtime) off oil, gas solenoid valve, with sound and light alarm signal. 4, via the feedwater system to a steam cycle water injection drum seat, gall direct flame furnace, the flame furnace heat absorption, the heat absorption of smoke tube furnace high temperature flue gas discharged water, boiler water becomes progressively heated steam, by after separation water separation means leads from the main steam valve. Henan party fast as a professional gas boiler manufacturer, has 70 years of design and manufacturing experience, customers throughout the country, the most recent of several large cooperative enterprises and 10 tons of gas hot water boiler, Zhengzhou University, Zhengzhou Yutong Bus with 10 tons of gas hot water boiler, Gongyi aluminum plant with 10 tons of gas steam boiler, your trust is fast Henan party's power in the service of idealism Henan party fast, quality-oriented principle never live up to your commitment to your trust!
Our company attaches great importance to the quality of wine, winemaking process steam requirements provided very strict, party fast boiler provides fully meet our needs, give us a brewery to provide strong support. --customer feedback
Steam Boiler vs Hot Water Boiler When it comes to the steam boiler vs hot water boiler, the operating principles are more or less the same. Both steam boilers and hot water boilers (also called hydronic boilers) involve the heating of water and creation of steam through the burning of fuel.Online chat
We have a largish bungalow with a potter ton statesman oil boiler. We are spending about £2200 per year on oil, and am thinking of changing to an air source heat pump. My question is how do I calculate how much electricity my oil boiler uses, to pump around the water and do whatever else it does to facilitate the oil boiler . Many thanksOnline chat
Henan Taiguo Boiler offer various industrial boilers, including Gas & Oil Fired Boiler, Coal Fired Boiler, Biomass Fired Boiler, Electric Heating Boiler, Thermal Oil Boiler,Steam Generator, Pressure Vessel, Hot Air Furnace, etc. Our products have been exported to more than 80 countries all over the world.Online chat
Forced Hot Water Heating. This type of system has a boiler for a heat source and heats the water inside the boiler. The heated water is sent up pipes throughout the house by either circulator pumps or zone valves. Fins in the baseboard then disperse the heat throughout the house.Online chat
Boiler Piping Flow & Pipe Sizing - It is important that the correct pump is selected in hot water boiler loops so that the correct velocity is achieved throughout the system. Too much velocity and the system will not be efficient because of Laminar flow issues.Online chat
Water Boilers. 1 - 40 1 to 40 of 47 products. Refine by | Top Brands. left hand navigation Skip to Search Results. Delivery & Pickup. Show all . 2-day delivery . Product Title USBLUEWAVE Electric Hot Water Boiler and Keeper Pot, Average rating: 5 out of 5 stars, based on 1 reviews 1 ratings.Online chat
How to adjust water temperature on boiler? I have a new Dunkirk DXL125 Hot water boiler that the Circulator pump isn't turning on when call gfor heat and Damper opens. Pump runs when direct wired. replaced the control board as well. Weil Mclain Ultra oil series 2 oil-fired-----setting high limit--seems boiler was pe-set to 140 degreesOnline chat
2 Common Boiler Formulas TABLE OF CONTENTS The boiler pressure is 100 psi and the boiler water temperature is 338°F. The latent heat is 881 Btu. What is the factor of evaporation? FE = SH + LH / 970.3 Microsoft Word - Johnston Boiler Company Boiler Glossary Author:Online chat
The chart below is based on an average Maryland home, and will help you answer how long will heating oil last. Adjust your estimates accordingly, erring on the side of caution to prevent running out of heating oil. In addition, we strongly suggest you keep your heating oil level above 30 gallons.Online chat
Pre-Inspection Checklist for Hot Water Heating or Hot Water Supply Boilers Page 5 of 5 REFERENCE COMPLIANCE YES NO Installation Requirements (continued) Section IV HG-709 When the boiler is located above the system and can be drained without draining the system, stop valves may be eliminated.Online chat
2. BOILERS Bureau of Energy Efficiency 27 Syllabus Boilers: Types, Combustion in boilers, Performances evaluation, Analysis of losses, Feed water treatment, Blow down, Energy conservation opportunities. 2.1 Introduction A boiler is an enclosed vessel that provides a means for combustion heat to be transferred into water until it becomes heated water or steam.Online chat
When the boiler detects that you've opened the faucet, it fires up and heats the water. If it's a central heating boiler, it usually has to pause from heating the central heating water while it's heating the hot water, because it can't supply enough heat to do both jobs at the same time.Online chat
Oil combination boilers eradicate the need for water tanks and cylinders which helps save on valuable space as they contain an internal hot water store to supply domestic hot water. Offered in a choice of either oil heating boilers or oil combi boilers, there is great availability in power and style depending on the demands of the property.Online chat
pressure hot water boiler 2019-03-19 About Us. Zozen Boiler main products include gas&oil boiler, coal-fired boiler, biomass boiler, thermal fluid heater and other series of more than 400 varieties of specifications.Online chat
The energy rate needed to evaporate 34.5lb of water at 212 °F (100 °C) in one hour. Equal to 33,475 BTU/h. 2 Boiler Horsepower to Btus Per Hour = 66950.7184: Boiler Horsepower to Imperial Tons of Refrigeration;Online chat